The vertical closed loop system consists of 180 vertical bores all over the premises to a depth of 80 meters. A minimum distance of 3 meters between any two bores is retained. Every bore has a 32mm outer diameter HDPE pipe U-loop and is connected in the central air conditioning plant room to the condenser water pipe system. A single U-Loop with a heat rejection capacity of 0.9TR results in a heat rejection capacity of 160TR from 180 vertical bores, resulting in reduction of cooling tower load and subsequent reduction in water consumption.
