  Overhead lines are generally used for electrical energy transmission. Also,
XLPE underground cable lines are generally used in the city center and the
crowded areas to provide electrical safety, so high voltage underground cable
lines are used together with overhead line in the transmission lines, and these
lines are called as the mixed lines. The distance protection relays are used to
determine the impedance based fault location according to the current and
voltage magnitudes in the transmission lines. However, the fault location
cannot be correctly detected in mixed transmission lines due to different
characteristic impedance per unit length because the characteristic impedance
of high voltage cable line is significantly different from overhead line. Thus,
determinations of the fault section and location with the distance protection
relays are difficult in the mixed transmission lines. In this study, 154 kV
overhead transmission line and underground cable line are examined as the mixed
transmission line for the distance protection relays. Phase to ground faults
are created in the mixed transmission line, and overhead line section and
underground cable section are simulated by using PSCAD. The short circuit fault
images are generated in the distance protection relay for the overhead
transmission line and underground cable transmission line faults. The images
include the RX impedance diagram of the fault, and the RX impedance diagram
have been detected by applying image processing steps. The regression methods
are used for prediction of the fault location, and the results of image
processing are used as the input parameters for the training process of the
regression methods. The results of regression methods are compared to select
the most suitable method at the end of this study for forecasting of the fault
location in transmission lines.
