quality:correction
Magnetic–hydraulic

A magnetic–hydraulic circuit breaker uses a solenoid coil to provide operating force to open the contacts. A magnetic–hydraulic breaker incorporates a hydraulic time delay feature using a viscous fluid. A spring restrains the core until the current exceeds the breaker rating. During an overload, the speed of the solenoid motion is restricted by the fluid. The delay permits brief current surges beyond normal running current for motor starting, energizing equipment, etc. Short-circuit currents provide sufficient solenoid force to release the latch regardless of core position thus bypassing the delay feature. Ambient temperature affects the time delay but does not affect the current rating of a magnetic breaker.

A large power circuit breaker, such as one applied in circuits of more than 1000 volts, may incorporate hydraulic elements in the contact operating mechanism. Hydraulic energy may be supplied by a pump or stored in accumulators. These form a distinct type from oil-filled circuit breakers where oil is the arc-extinguishing medium.