Will this work as a direct replacement for a 2100T
349489
I wish I could answer that, but I don't know. I recommend you call the company or go to their web site. (I had to call them.)
349490
The 2100T and 2W are both "2 wire" smoke detectors. This means that the device gets it power from the same two wires it provides an initiating signal to the zone. Therefore "2 wire" detectors must be designed in such a way that its parameters fully match the design parameters of the zone and also of the panel when configured as a smoke zone. Since these two devices are both made by System Sensor and the 2W is intended to replace the 2100 in its line of detectors it is likely that the parameters match. The issue is that "2 wire" detectors must be listed (usually by UL) to work with the specific panel it is being connected to AND the panel must be listed to work with that particular detector. This is called cross listing. Listing is done by the testing agency (i.e. UL) by actually testing the specific detector on the specific panel. It is more common than not that the manufacturer of an older panel has not updated their panel listed by testing a newly released detector with that panel. In addition it is likely the new detector was not tested while being connected to an older panel. Note also, that a particular model panel's listing might be updated to be cross listed with a newer smoke detector but existing units in the field do not automatically have their listings updated - a panel firmware upgrade would be required. Though not knowing the panel being utilized the answer is probably no. It is likely that the 2W will work fine but without the cross listing one cannot be certain of this and installing the 2W in a panel it has not been cross listed for is a violation of NFPA standards and in most jurisdictions against local and/or state statutes.
942029
Yes, be careful though of the regular source 210 designation, comes with a few less features like a fan and the like.
319889
The housings are different. It won't be a direct replacement. You will have to do a little plumbing. Volume and flow would be fine.
2059092
Yes, it will. This replacement is stick-simple and only takes about 15-20 minutes from start to finish. Often, only one of the two modules (left and right...) are damaged but you're smart to replace both. There are a couple of 'how to' videos on YouTube that illustrate how to do this.
2055307
Yes, it is a direct replacement. The wires are exactly the same color as the old one.Connect the new one one wire at a time. This was a very good mod to my motorhome.
1624392
I believe the replacement should work. I think the 550 and 550VA designations refer to the Volt-Ampere ratings of the units.
676666
Not sure, but I would check "dieseltechron" on YouTube and see if he has your year ficm swap. Hope that helps.
87032
It will work with any 12v system.If you are asking if it is a direct replacement fit I do not know.
230555
It fit my #SM-T210 perfectly.If there isn't much of a big difference in the 210 & 217 it might work.
246322
Not sure. I did not have the model you mentioned. But, the description within this replacement best describes what it does replace.
888114
Yes, it'll work. I have the same unit and needed to replace my transducer once and this is a direct replacement.
328442
We basicly looked for the configuration that matched so it was really easy to replace and worked great. I would make sure it matches up to your old one and it should be fine.
1843996
Check the docs on your specific model, this is a direct replacement for the tn450 toner cart.
405276
The 210 l looks totally different than my 405 so I think that it will not work.
541666
No it will not, you have to get the exact replacement part.. They have different types of connections for each generation.. I already made that mistake thinking I was getting a deal because of the price tag. Hope this helps
1737888
Not sure, but I would try putting model/make into google and put in the words replacement parts. See what comes up. Good luck!
1484469
Yes this is an exact replacement for this part. I JUST REPLACED THE 137645 WITH THE 130794.