Does anyone use this unit wired up to their house panel?
1017533
I feel it is a bit small to wire into the house panel. Of course if you manage your power demand you could get by. I use this unit to supply power exclusively to my computers, telephone, sound system, etc. Things that need a true sine wave. The unit lives close to the battery bank with the 110v output running into the house, about 35 ft.
1017534
I use this unit just like a stand-alone generator. A heavy gauge wire connects the outlet of the inverter to the generator input of a subpanel wired with the critical circuits intended to be powered in the event of an electric outage. The subpanel should be wired to insure a disconnect from the power company so no power feedback occurs over company power lines. The Xantrex includes a ground fault circuit breaker so no additional ground connection is required when attaching the unit to the subpanel. The connecting cable should include a female twist lock connector which attaches to a male input connector to the subpanel, just the same as a cable used to connect a generator to a sub-panel. I use this unit just like a stand-alone generator. A heavy gauge wire connects the outlet of the inverter to the generator input of a subpanel wired with the critical circuits intended to be powered in the event of an electric outage. The subpanel should be wired to insure a disconnect from the power company so no power feedback occurs over company power lines. The Xantrex includes a ground fault circuit breaker so no additional ground connection is required when attaching the unit to the subpanel. The connecting cable should include a female twist lock connector which attaches to a male... » Read More I use this unit just like a stand-alone generator. A heavy gauge wire connects the outlet of the inverter to the generator input of a subpanel wired with the critical circuits intended to be powered in the event of an electric outage. The subpanel should be wired to insure a disconnect from the power company so no power feedback occurs over company power lines. The Xantrex includes a ground fault circuit breaker so no additional ground connection is required when attaching the unit to the subpanel. The connecting cable should include a female twist lock connector which attaches to a male input connector to the subpanel, just the same as a cable used to connect a generator to a sub-panel. « Show Less
1017535
Does this unit have hardwire ac output? If it does not, how would I wire this into an off grid ac electrical panel to supply circuits for electrical outlets and lights for a small cabin. Note there is no electrical company power lines coming into the panel). Thanks!
1017536
You could as long as it was isolsted from the utility power grid with a transfer switch or equal, keep in mind thstit is only 120vac output and your house panel is most likely 120/240. Better use is for emegency backup seeSunbyrd.com or kcbyrdelectric.com will link you there. We use them in a stand alone backup systemtnx, kee.
1017537
I have wired it into a 60A sub-panel using a pig-tail connector to the main lugs, and power both breaker poles from the output so they are all powered. 2-pole breakers would not work in this configuration of course. 15-amp circuit breakers distribute the load as needed, while providing fault protection on the output. The GFI built into the unit also protects the entire system from ground-faults, which is nice.My sub-panel is completely isolated from any grid power, so I don't use a transfer switch or interlock.The grounding should occur at the Xantrex, since this has a bonded neutral / ground configuration. I have wired it into a 60A sub-panel using a pig-tail connector to the main lugs, and power both breaker poles from the output so they are all powered. 2-pole breakers would not work in this configuration of course. 15-amp circuit breakers distribute the load as needed, while providing fault protection on the output. The GFI built into the unit also protects the entire system from ground-faults, which is nice.My sub-panel is completely isolated from any grid power, so I don't use a transfer switch or interlock.The grounding should occur at the Xantrex, since this has... » Read More I have wired it into a 60A sub-panel using a pig-tail connector to the main lugs, and power both breaker poles from the output so they are all powered. 2-pole breakers would not work in this configuration of course. 15-amp circuit breakers distribute the load as needed, while providing fault protection on the output. The GFI built into the unit also protects the entire system from ground-faults, which is nice.My sub-panel is completely isolated from any grid power, so I don't use a transfer switch or interlock.The grounding should occur at the Xantrex, since this has a bonded neutral / ground configuration. « Show Less
1582684
No, however I use a zwave outlet and just plug in a cd converter with an appropriate relay. Very simple
1295134
Nope. But my experience with it is, its a hit or miss if you use it. I just wire mine directly.
1415473
I wired mine using the existing 40-yr-old, 3-switch wall unit. I think any device that causes the electricity to be fed to the correct wires, when you want it fed there, will do.
274536
It didn't end up working with my house because you have to wire it in. I thought it was battery operated. Sorry!!
1875407
No it does not. I tried to find a connection for an adapter for house current, but could not find one.
154475
I have mine plugged into a regular household 3 prong outlet, and it is working just find for me.
875995
No. the system is hard wired. You have to run the wires through your home or office.
2077686
Mine works well but you could replace it with automation software from HCA (http://www.hcatech.com/) and a power line interface from Insteon (PowerLinc).
478452
No......as far as I can tell. I have it plugged into the 110 here at the house.
350479
Hmm That does sound like a serious issue! I cannot say that I have had that problem yet and I have 8 units installed in my house. It sounds to me like the unit is placed on a circuit that is beyond the recommended load which can easily happen. In other words, this issue sounds like people are using the units on circuits that were already poorly wired. Just my thoughts.
1021457
I have mine plugged into a standard wall plug and have had no issue with it throwing the circuit breaker...
2174866
No I do not but I do keep it plugged into a surge protector. So far, so good.
715645
While we've not had the occasion to do this, it shouldn't be a problem. The wires connect by just pushing into the unit and plugging the unit in. If you have the wiring at the second location, you should be good to go.
831018
no,i wired mine into the bathrooms light switch and then left the unit on. that way it would come on anytime someone used the bathroom.
1672194
I just plug them in...in various rooms. Then I put them on the same channel and test them. They work fine so long as the outlets are grounded to the same circuit breaker panel. I have two large panels, so It's been a little tricky as one side of my kitchen and one child's room is wired to one panel, while the other side and other child's room is on another. So I ended up with 2 intercoms in the kitchen. Most homes only have one main panel, so it will probably work fine in most homes.
404170
Yes. I wired mine to the existing switch. If you don't have one, just add one inline to your power panel.