I have a 30 amp generator - Can I use it with 50 amp transfer switch and inlet box? Need 50 amp equipment just in case I upgrade my generator later.
1102426
Yes you can.this is a great box but a pain to close after connecting wires.should be AWG #6
1102427
As was stated it is a good idea. Just make sure that the wire from the inlet is also sized for 50 ampAnother option instead of using an adapter would be to get a cord made up with the right ends for the generator to the inlet
1102428
Yes you can. It can handle 30 amps with no problem. But don't use a 30 amp transfer switch for a 50 Amp generator- BIG trouble!
1102429
One last thing, you will probably need an adapter for the cable. A 50 amp generator usually has both types of outlets, 30 and 50 amps. A 30 amp generator only has a 30 amp outlet and it has a different type off plug.
1102430
Yes. I have two generators that hook up into this rig. It works. One is a 50 amp/ 10,000 watt welder/ generator. The other is a 30 amp/ 5600 harbor freight turd. It handles both. Just make sure your plug ends match the box/ generator twist lock.
840175
This was a 30 AMP plug. I purchases a 50' generator cable. The cable is mounted in the suspended ceiling of the basement. The female end of the cable is hanging from the ceiling in front of the transfer swirtch. The other end actually runs outside and hangs under the deck where the generator would go. I didn't purchase a seperate 30 amp plug. It's part of the 50' cable.Hope this helps.
1695217
Yes as long as the generator has the 30amp outlet. If the generator doesn't have the 30amp outlet you can use an adapter or just use a good 10 or 12 gage cord.
326033
I agree with James, assuming your generator is peak 5500, you should be fine. Remember that the transfer switch likes to balance the load, half on one side A&B circuits and half on E&F circuits (C&D is for the 220volt circuit). Check out this web page, look at the Q&A section. http://www.electricgeneratorsdirect.com/Reliance-Controls-20216A/p1113.html Switch is super easy to install, gauge works well to watch wattage load too. Be sure your amperages are right, that will trip the gen each time if not.
450349
There are two inputs that this can switch between. One input is a 100amp feed from your breaker panel, the other is a 60amp input you wire to a generator input of your selection. Typically, you'd then wire a single output to a sub panel. Bear in mind you'll only ever have 60 or 100 amps coming into that sub panel, which for most people is adequate for "critical" loads ( fridge, freezer, well pump). I have mine feeding a 20 space breaker panel. There are no "circuits" in this unit as there are in many transfer switches that combine a switch like this with a loads panel. This is just the switch. Consult a professional electrician for wiring it together. There are two inputs that this can switch between. One input is a 100amp feed from your breaker panel, the other is a 60amp input you wire to a generator input of your selection. Typically, you'd then wire a single output to a sub panel. Bear in mind you'll only ever have 60 or 100 amps coming into that sub panel, which for most people is adequate for "critical" loads ( fridge, freezer, well pump). I have mine feeding a 20 space breaker panel. There are no "circuits" in this unit as there are in many transfer switches that combine a switch like this with a loads panel.... » Read More There are two inputs that this can switch between. One input is a 100amp feed from your breaker panel, the other is a 60amp input you wire to a generator input of your selection. Typically, you'd then wire a single output to a sub panel. Bear in mind you'll only ever have 60 or 100 amps coming into that sub panel, which for most people is adequate for "critical" loads ( fridge, freezer, well pump). I have mine feeding a 20 space breaker panel. There are no "circuits" in this unit as there are in many transfer switches that combine a switch like this with a loads panel. This is just the switch. Consult a professional electrician for wiring it together. « Show Less
1794683
No it does not. You likely have a 100 or 200 amp electric service and the generator has an output of about 30 amps. It should be able to handle your essential circuits though using an 8-10 circuit transfer panel
312412
no. there is a voltage limiter on the unit, that turns on after a supply check is done. that is why they sell a 30 amp unit and a 50 amp unit. you can go from a 50 amp to a 30 amp supplt, but not visa versa. you can always adapt down, but not always up.
450348
There are two inputs that this can switch between. One input is a 100amp feed from your breaker panel, the other is a 60amp input you wire to a generator input of your selection. Typically, you'd then wire a single output to a sub panel. Bear in mind you'll only ever have 60 or 100 amps coming into that sub panel, which for most people is adequate for "critical" loads ( fridge, freezer, well pump). I have mine feeding a 20 space breaker panel. There are no "circuits" in this unit as there are in many transfer switches that combine a switch like this with a loads panel. This is just the switch. Consult a professional electrician for wiring it together.
1084192
You will need a double breaker with a minimum of 25 amp on each side. I have a double 30 on 1 panel and a double 40 on the other (I have 2 hookups) The Generator has its own breaker as well if over drawn.
1280799
You do not want this model. It is only rated at 5000 watts and 20 amps. Assuming your generator is rated at 30 amps, purchase the largest 30 amp box you can. The amps are just as important as the watts. You want to supply as many circuits as you can. Take into account that the chances of all your appliances running at peak wattage all at the same time are slim to none. The most important thing to know is to turn them on in the proper sequence. Turn on the appliances with the highest load first, waiting for the wattage spike. Turn them on one at a time until the wattage drops and you should be good. When it comes to electricity, bigger is better. You do not want this model. It is only rated at 5000 watts and 20 amps. Assuming your generator is rated at 30 amps, purchase the largest 30 amp box you can. The amps are just as important as the watts. You want to supply as many circuits as you can. Take into account that the chances of all your appliances running at peak wattage all at the same time are slim to none. The most important thing to know is to turn them on in the proper sequence. Turn on the appliances with the highest load first, waiting for the wattage spike. Turn them on one at a time until the wattage drops and you should... » Read More You do not want this model. It is only rated at 5000 watts and 20 amps. Assuming your generator is rated at 30 amps, purchase the largest 30 amp box you can. The amps are just as important as the watts. You want to supply as many circuits as you can. Take into account that the chances of all your appliances running at peak wattage all at the same time are slim to none. The most important thing to know is to turn them on in the proper sequence. Turn on the appliances with the highest load first, waiting for the wattage spike. Turn them on one at a time until the wattage drops and you should be good. When it comes to electricity, bigger is better. « Show Less
446048
One that will transfer 30 amps of power and break it down into about 8 to 10 curkits in your existing main pannel with a manual transfer switch But you will need to shut the main in your existing pannel off befor turning on the auxillery pannel. I think Amazon sells the auzillery pannels also, hope this helps. Milt
1211221
Yes you can by plugging a 30 amp adapter pigtail into the 50 amp surge protector. Works fine. The manufacturer supplied me this information
938581
You have a 30 amp cable rated for 250 volts which is 7500 watts. (AxV=W) When it says 8750 max it means it will not blow the breaker during an inrush when something starts (up to 8750W). The cable will also handle this. Just watch the amp meter on the generator to see what you are running at. Test it when the weather is nice. If it is more than 7000 W your generator is too small. Your option is to shut off some breakers or get a larger generator and a 40 A cable.I assume you have a transfer switch if it connected to the main panel.
1609393
No, I put a 30amp breaker in the main panel to feed one side of this switch. The other side will be wired to a generator. Hope this helps.
1928924
Here are some notes I used with my generator. It is rated the same as yours. I use #10 wiring for the 220V/30A plug on the generator. #10 wire is rated at 30A and #8 wire is rated at 50A. For 220V: 5500 watts = 25A 8250 watts = 37.5A For 120V: 5500watts = 45A 8250 watts = 69A Go to http://www.calculatoredge.com. Go to the "Electrical" tab and "Voltage-Current-Resistance-Power Calculator" tab to find the calculations you need. As I stated I use the 10ga.wire hooked to the 220V/30A plug and I split it in the house to (2) 110V circuits. I run 2 refrigerators, sump pumps, couple of lamps, and the furnace if needed. I only use it for essential items during power outages. I don't even get to capacity of the generator with all things running. So calulate first what you are running to make sure the circuit and generator is not overloaded. I hope this helps you out. Best Regards.
2203337
getting a 50amp breaker isnt what you want.. you want the 30amp if you running a 30amp system im sure they still sell a 30 - 35A kinds of these but im using this and a 35amp breaker on my car system 14v 30a and they work great but the terminals are kinda small and id even say teh yare a bottle-neck for my 0 g cable
2253987
No 30 Amp will work fine, 50a is the output but not at 220v. I have mine on a 20a with no problem.